Shadowing Effect in Fire Resistance Design According to EN 1993-1-2
Tips & Tricks
For unprotected I‑sections, the standard provides the correction factor ksh according to Equation 4.26a in Chapter 188.8.131.52 (2) to consider the shadowing effect. A term [Am/V]b is used there. This section factor includes Am, which represents the box enclosing the cross‑section (Index b = boxed). In the case of a three-sided fire exposure (a girder with massive ceiling), the flange surface unexposed to fire is not taken into account when determining [Am/V]b.
|Three-sided:||[Am/V]b = (h+h + b)/V|
||[Am/V]b = (h+h + b+b)/V|
h and b are outer dimensions of the cross-section.
There is no information in the standard regarding the determination of the correction factor ksh for three-sided fire exposure. In the RF‑/STEEL EC3 add‑on module, the correction factor ksh is always considered.
Do you have any questions or need advice?
Contact us or find various suggested solutions and useful tips on our FAQ page.